The Ohio State University had a ventilation trailer constructed in 2001 to help teach basic livestock building ventilation concepts and familiarize livestock producers with air measuring and monitoring devices. The trailer had three ventilation fans and three air inlet designs. Key concepts covered in the lecture portion of ventilation workshops included: types of building ventilation, ventilation terminology, air speed, proper static pressure, ventilation rates for animals of various sizes, fan performance, fan controller performance, and voltage curves. Workshop attendees were provided ventilation monitoring equipment such as a manometer, high/low thermometer, hot wire anemometer, smoke sticks, smoke matches and an infrared thermometer and encouraged to use them with the ventilation trailer. Twenty years after its construction, the trailer has been updated with new equipment and is still used with students and livestock companies. The trailer was built with financial help from the Ohio Pork Council, Ag Credit, Farm Credit Services, Farmer Boy Ag Supply, Curry Lumber, and the OSU College of Food, Agriculture, and Biological Engineering.
The authors are solely responsible for the content of these proceedings. The technical information does not necessarily reflect the official position of the sponsoring agencies or institutions represented by planning committee members, and inclusion and distribution herein does not constitute an endorsement of views expressed by the same. Printed materials included herein are not refereed publications. Citations should appear as follows. EXAMPLE: Authors. 2022. Title of presentation. Waste to Worth. Oregon, OH. April 18-22, 2022. URL of this page. Accessed on: today’s date.
Recent research has shown that over half of nitrogen excreted by chickens is lost into the atmosphere via ammonia volatilization before the litter is removed from poultry houses. Large quantities of particulate matter and volatile organic compounds (VOCs) are also emitted from animal rearing facilities. During the past decade we have developed and patented an acid scrubber for capturing ammonia, VOCs and dust from air exhausted from poultry and swine barns. The objectives of this project were; (1) to re-design the scrubber to improve the ammonia removal efficacy, (2) conduct full-scale testing of the scrubber under controlled conditions at various ventilation rates, (3) evaluate the cost, practicality and efficacy of various acids for scrubbing ammonia, and (4) install scrubbers on exhaust fans of poultry houses located in Virginia and Arkansas and measure the efficiency of ammonia removal from the exhaust air. The efficiency of ammonia removal by the scrubber varied from 55-95%, depending on the type of acid used, air flow rate, and the internal scrubber configuration. This technology could potentially result in the capture of a large fraction of the N lost from AFOs, while simultaneously reducing emissions of bacteria, dust, and odors, which would improve the social, economic, and environmental sustainability of poultry and swine production.
The objectives of this project were; (1) to re-design our ammonia scrubber to improve the ammonia removal efficacy, (2) conduct full-scale testing of the scrubber under controlled conditions at various ventilation rates, and (3) evaluate the cost, practicality and efficacy of various acids for scrubbing ammonia.
Acid scrubber developed by USDA/ARS in Fayetteville, AR, for reducing ammonia, dust and odor emissions from animal rearing facilities.
What Did We Do?
During the first year of this project the main task of our team was to re-design the ammonia scrubber developed and patented by Moore (2007). A full scale prototype was constructed of wood and a series of tests were conducted to evaluate various configurations on air flow and static pressure drop in tests conducted in a machine shop. The scrubber was connected to a 48” variable speed poultry fan. Air flow was measured using a fan assessment numeration system (FANS unit). Static pressure difference was measured using a Setra 2601MS1 differential pressure sensor. The effects of slat angle, number and arrangement of slats, and thickness of cool cell material were evaluated.
Following the initial testing a fiberglass mold was made and six scrubbers were constructed. One of these was used to evaluate the effectiveness of water, strong acids, acid salts, and a neutral salt on scrubbing ammonia. Anhydrous ammonia was metered out into a distribution system located within the fan at a sufficient rate to result in 25 ppm NH3 in the plenum between the fan and the dust scrubber. Evaluations of each acid were made with the variable speed fan set at 60 and 40 Hz, which corresponded to air flows of approximately 8,000 and 5,000 cfm, respectively. A stainless steel star sampler was used to take air samples from the plenum and from the air exhausted from the scrubber. Ammonia concentrations were measured using a photoaccustic multigas analyzer (Innova 1412). All personal involved in this testing wore respirators equipped with NH3 cartridges. Three 2-hour trials were conducted with solutions of the following acids at both 40 and 60 Hz: alum, aluminum chloride, ferric sulfate, ferric chloride, sodium bisulfate, sulfuric acid, hydrochloric acid, phosphoric acid, and nitric acid. The effects of water and calcium chloride were also evaluated. For these trials the amount of each acid added was equivalent to 2 liters of concentrated sulfuric acid.
In addition to measuring inflow and outflow ammonia levels, the mass accumulation of ammonia in both the dust and acid scrubber reservoirs was determined by analyzing the contents for ammonium using an auto-analyzer. Twenty ml aliquots of the scrubber solution were taken at times 0, 1 and 2 hours for ammonia and pH measurements. These data were used to validate that the difference in inlet and outlet ammonia were, in fact, due to accumulation of NH3 in the scrubber. Notes were also taken on each chemical’s ease of use and potential for problems. For example, some dry acids did not readily dissolve and some strong acids, like sulfuric acid, had very strong exothermic reactions. Salts of aluminum and iron become aluminum and iron hydroxides at high pH which have the potential to clog cool cell material.
Another performance issue that was monitored was the loss of fine droplets (mist) from the scrubber. When dealing with high air volumes and small droplet sizes, there is a potential for mist to exit the system, resulting in not only the loss of N, but of the acid used to scrub NH3. In order to measure mist loss, five 12.5 cm Whatman 42 filters were attached on a wire cage on the exhaust of the scrubber. These filters were placed in a 50 ml centrifuge tub at the end of each trial and shaken with 25 ml of DDI water, which was analyzed for ammonium, along with sulfate, chloride, nitrate, or phosphate, depending on the acid used.
What Have We Learned?
Early on in this research we learned that two scrubbers (a dust scrubber and an acid scrubber) were needed rather than one. If the dust isn’t removed from the exhaust air of poultry houses, then a large amount of the acid will be wasted neutralizing the dust.
We found that the relationship between slat angle and pressure drop was exponential and the angle that would maximize particle collisions on a wet surface while minimizing pressure drop was 45o. We also found that as the number of rows of slats increased the effect on pressure drop was linear. The final configuration chosen was eight rows of slats in the dust scrubber and three rows of slats in the chemical scrubber, followed by one or two 6” thick layers of cool cell material. The pressure drop using this configuration was about 0.1” of water at 5,000 cfm and 0.3” of water at 8,000 cfm.
All of the acids scrubbed ammonium from air, whereas water and calcium chloride only worked for a very short period of time. The iron (Fe) and aluminum (Al) compounds tended to work a little better than the other acid salts or the strong acids. We believe this is due to Fe and Al compounds coating the cool cell material. Although no difference was observed in the static pressure during these short tests, we believe Al and Fe hydroxides would eventually form and may clog the cool cells. Due to the inherit danger in dealing with strong acids, we concluded that an acid salt that did not contain Al and Fe, such as sodium bisulfate, would be used for our research in the future. This product is sold under the tradename PLT for a poultry litter treatment and is readily available to poultry growers.
Four NH3 scrubbers will be attached to sidewall fans of a commercial broiler house located in Madison County, Arkansas. The efficacy of these scrubbers for reducing ammonia, volatile organic compounds (VOCs), and particulate matter will be evaluated. We will also measure the amount of sodium bisulfate, water and electricity used by the scrubbers, as well as the mass of nitrogen captured. A cost-benefit analysis will be performed based on this data. Data on the efficacy to scrub ammonia will also be conducted on farms in DE, VA, and PA.
This research was funding by USDA/ARS and by grants from USDA/NRCS and the National Wildlife Foundation. The authors would like to thank the hard work and great ideas supplied by Scott Becton and Jerry Martin, without which this scrubber could not have been built.
The authors are solely responsible for the content of these proceedings. The technical information does not necessarily reflect the official position of the sponsoring agencies or institutions represented by planning committee members, and inclusion and distribution herein does not constitute an endorsement of views expressed by the same. Printed materials included herein are not refereed publications. Citations should appear as follows. EXAMPLE: Authors. 2013. Title of presentation. Waste to Worth: Spreading Science and Solutions. Denver, CO. April 1-5, 2013. URL of this page. Accessed on: today’s date.
Air emissions from animal housing systems are being examined more closely for ways to mitigate potentially harmful gases. Wet scrubbers are one way to remove pollutants from air being exhausted from mechanically ventilated buildings. The materials on this page were developed to assist educators and professors who include wet scrubbers as a topic in their classrooms or educational programs.
These materials were developed by the Air Quality Education in Animal Agriculture (AQEAA) project with with financial support from the National Research Initiative Competitive Grant 2007-55112-17856 from the USDA National Institute of Food and Agriculture.
For questions about the materials on this page contact Dr. Linying Zhao, Ohio State University (email@example.com). For questions about the AQEAA project, contact Dr. Rick Stowell, Unviersity of Nebraska (firstname.lastname@example.org).
If you have presentations, photos, video, publications, or other instructional materials that could be added to the curricula on this page, please contact Dr. Zhao or Jill Heemstra (email@example.com).
Manage Cookie Consent
To provide the best experiences, we use technologies like cookies to store and/or access device information. Consenting to these technologies will allow us to process data such as browsing behavior or unique IDs on this site. Not consenting or withdrawing consent, may adversely affect certain features and functions.
The technical storage or access is strictly necessary for the legitimate purpose of enabling the use of a specific service explicitly requested by the subscriber or user, or for the sole purpose of carrying out the transmission of a communication over an electronic communications network.
The technical storage or access is necessary for the legitimate purpose of storing preferences that are not requested by the subscriber or user.
The technical storage or access that is used exclusively for statistical purposes.The technical storage or access that is used exclusively for anonymous statistical purposes. Without a subpoena, voluntary compliance on the part of your Internet Service Provider, or additional records from a third party, information stored or retrieved for this purpose alone cannot usually be used to identify you.
The technical storage or access is required to create user profiles to send advertising, or to track the user on a website or across several websites for similar marketing purposes.